Posts Tagged Windows COM port error
Honeywell’s Process Instrument Explorer (PIE) configuration software used for configuring UDC controllers and the UDA analytical controller communicates with the instruments via RS-485, Ethernet, or Infrared (IR).
Since most newer PCs don’t ship with built-in serial ports to connect an IR adapter, you can use a USB-to-RS-232 converter, and then connect using the Actisys serial-to-infrared adapter (ACT-IR220L+). The USB converter will plug directly into your PC’s USB port, but install on a virtual COM port.
Here’s where it gets tricky: That COM port has to match the COM port used in PIE, and PIE doesn’t support ports above COM8.