Posts Tagged upper range limit
Wet rhymes with Set (or how to remember LRV/URV configuration prompts)
Posted by danstips in Configuration, Honeywell, Installation, Level Transmitters, Pressure, Pressure Transmitters, pressure transmitters, Siemens, Transmitters on July 26, 2013
Lots of people like the pushbuttons on industrial pressure transmitters because the basic settings that every transmitter needs can be set up without a HART communicator. This includes things like the tag name, engineering units, LRV (Lower Range Value, the zero, or what 4.0mA represents), URV (Upper Range Value, the span, or what 20.0mA represents) and damping (an average or filter factor that dampens noise).
On the new Honeywell ST700/ST800 series smart transmitters, the tag name and engineering units are easy to configure and self explanatory, but I seem to stumble when setting up the LRV and URV because I’m faced with a non-descript choice. There’s two sets of options (under Transmitter Setup, not Calibration):
OK, either configures an LRV or a URV value, but which is which? What’s the difference?
How do I set upper range value and lower range value on a Siemens pressure transmitter?
Posted by danstips in Configuration, Installation, Level Technology, Pressure, Pressure Transmitters, Siemens, Transmitters on February 21, 2012
A customer needed to re-range a Siemens SITRANS P DS III transmitter without applying pressure. He’d read my earlier blog post about using the pushbuttons to program the DS III (Pressure Transmitter Pushbuttons to the Rescue!), and where to find the Z-fold instruction sheet.
All was going to plan, until he started looking for the settings for lower range value (LRV) and upper range value (URV). And then, in an all-too-familiar scenario, he hit a roadblock. The instructions don’t actually mention URV and LRV, the terms he’s familiar with, by name or acronym. So what’s a guy to do?