Posts Tagged process control strategies
What does NAMUR NE 43 do for me?
Posted by danstips in Honeywell, Level, Level Technology, Measurement, NAMUR, Pressure, Pressure Transmitters, pressure transmitters, Process terminology, Siemens, Standards, Transmitters on February 17, 2012
People have asked me about setting fault alarms in level transmitter analog signals at 2mA or 3mA levels. What they typically don’t understand is that a two-wire transmitter uses the electrical current below 3.6 mA for its own power and operation. So, a 2.0 mA or 3.0 mA fault indication just isn’t possible. At these low currents, there wouldn’t be enough power to generate the fault indication signal and to keep the transmitter functioning properly. Read the rest of this entry »