Posts Tagged low level
How do I set upper range value and lower range value on a Siemens pressure transmitter?
Posted by danstips in Configuration, Installation, Level Technology, Pressure, Pressure Transmitters, Siemens, Transmitters on February 21, 2012
A customer needed to re-range a Siemens SITRANS P DS III transmitter without applying pressure. He’d read my earlier blog post about using the pushbuttons to program the DS III (Pressure Transmitter Pushbuttons to the Rescue!), and where to find the Z-fold instruction sheet.
All was going to plan, until he started looking for the settings for lower range value (LRV) and upper range value (URV). And then, in an all-too-familiar scenario, he hit a roadblock. The instructions don’t actually mention URV and LRV, the terms he’s familiar with, by name or acronym. So what’s a guy to do?