Posts Tagged differential pressure transmitter
A while ago, I got a call from a customer who was having trouble with a differential pressure transmitter. He was using a draft range DP transmitter to measure the pressure in a combustion chamber, so it could be controlled with a damper. He had one port connected to the combustion chamber with impulse tubing, and the other (low side) was left open to the atmosphere.
He’d noticed that when a fork truck or other vehicle sped past the furnace – the transmitter was mounted next to a traffic lane — it cause the furnace pressure to momentarily dip downward, and cause the damper to oscillate.
He figured out that the air movement provided by the passing vehicle was creating a momentary pressure pulse on the low side port. These air movements were creating difficulty in maintaining furnace pressure.
So, he asked me, “How can we dampen the effect of the momentary pressure pulse?”
It was bound to happen sooner or later.
I took a call from a customer who needed to replace a garden variety differential pressure transmitter… with one exception: He needed Honeywell’s DE digital protocol for communicating to his DCS. The DE protocol is still great, but since so many installations today use HART or Foundation Fieldbus, all of our in-stock pressure transmitters had a HART communication card – a critical mismatch to what the customer needed.
A year ago, we would have been stuck rush-ordering a unit from the factory, with all the attendant delays and expediting charges, because you couldn’t swap out a comms card without making the transmitter’s hazardous approval invalid.
What could we do?
Read the rest of this entry »