Avoiding the Obstacles of Tending an Aging Paperless Recorder
Posted by danstips in Honeywell, Trendview X-Series Paperless Recorders, Troubleshooting on October 31, 2016
Written by: Dan Weise
It’s been about a decade since the Honeywell Trendview X-Series paperless recorders were first introduced. And as with any product, you can expect some routine maintenance and service requirements that come with age.
We’ve summarized the top four obstacles you may face when tending to your aging paperless recorder, and how you can overcome them to further maximize the lifespan and functionality of your device.
Before you start, make sure you have a printed record of your paperless recorder’s custom configurations in case you need to restore them to your unit.
1. Changing the Clock Battery
If your paperless recorder is getting old, the battery may be ready to be swapped out. Your recorder uses a standard CR2032 lithium battery that is both inexpensive and readily available at most drug stores.
Although this appears to be a simple solution, I’ve noticed when I change out the battery, the system resets the clock to January 1, 2003.
If you haven’t enabled security, you can just login and change the time. But, this can pose a problem if your recorder uses the ESS extended security (usually a pharmaceutical requirement). When an ESS-enabled recorder resets back to Jan 1, 2003, no user, not even an administrator, can get access to the setup because the valid period for all passwords appears to have expired.
In order to avoid this problem, it is best to plan ahead before attempting to replace the clock battery.
How to Avoid Honeywell Process Instrument Explorer (PIE) Software Communication Errors
Posted by danstips in Analytical Measurement Devices, Communications, Configuration, Control, Loop Controllers, Process Automation Controllers, Serial, Software, Troubleshooting on August 26, 2016
Honeywell’s Process Instrument Explorer (PIE) configuration software used for configuring UDC controllers and the UDA analytical controller communicates with the instruments via RS-485, Ethernet, or Infrared (IR).
Since most newer PCs don’t ship with built-in serial ports to connect an IR adapter, you can use a USB-to-RS-232 converter, and then connect using the Actisys serial-to-infrared adapter (ACT-IR220L+). The USB converter will plug directly into your PC’s USB port, but install on a virtual COM port.
Here’s where it gets tricky: That COM port has to match the COM port used in PIE, and PIE doesn’t support ports above COM8.
Chemical Seal Assemblies Available from Lesman Stock
Posted by danstips in Pressure Gauges, Service, WIKA on July 22, 2016
Chemical seals and fills are often necessary to protect your process instrumentation from harm. But the wait for a custom gauge-and-seal, switch-and-seal, or transmitter-and-seal combination could be an issue, keeping your process offline for longer than necessary, or costing a premium for quick delivery.
We’ve removed the potential for downtime and rush charges with our WIKA-certified assembly station, and improved stock of most popular transmitters, switches, gauges, diaphragm seals, and fill fluids. Lesman customers can experience next-day delivery on custom assemblies from in-stock instrumentation.
Get More Combustion System Data into your PLC
Posted by danstips in Combustion, Communications, Flame Safeguard Controls, Flame Safety, Honeywell, Modbus on July 14, 2016
Written by: A.J. Piskor
Traditionally, combustion control panels have been living in a hard-wired world. More often than not, the status of a burner system is communicated by indicator lights on a Flame Safeguard (FSG) terminal.
With the increased use of Programmable Logic Controllers (PLCs) controlling all aspects of a combustion system, customers are demanding more information from the FSG, as many operators manage their systems from a centralized control room.
While some customers have traded in their indicator lights for relays with dry contacts that feed back into their PLC, other customers are looking to simplify the communication between the FSG and PLC, while extracting more information on the operation of their burner system.
Here, we will go over some examples of technologies that are available today, and how you can get the information you need to where you need it.