Archive for category Standards
People have asked me about setting fault alarms in level transmitter analog signals at 2mA or 3mA levels. What they typically don’t understand is that a two-wire transmitter uses the electrical current below 3.6 mA for its own power and operation. So, a 2.0 mA or 3.0 mA fault indication just isn’t possible. At these low currents, there wouldn’t be enough power to generate the fault indication signal and to keep the transmitter functioning properly. Read the rest of this entry »
Ever wonder if you can mix brands of thermocouple heads, transmitters, or junction blocks? The other day, I was trying to figure out if I could, and I ran into a spec I didn’t understand – DIN Form B. So, what exactly is DIN Form B, and how does it relate to thermocouple heads, transmitters and junction blocks?