Archive for category Installation
People will fire up a new UDC 1/4 DIN loop controller, like a UDC2500 or UDC3200, and discover that the lower display periodically flashes an error code: UNPLUG. But what does it mean? Is something wrong?
A search of the pdf version of the manual hints that the Modbus Ethernet communications is involved:
The Ethernet status screen shows the network status of the Ethernet Link. This may be accessed either via Ethernet or via Infrared Communications. For example, if the Ethernet cable is unplugged, then the instrument cannot send up the EUNPLGED diagnostic message via Ethernet.
But the word UNPLUG is nowhere else in the manual.
As energy costs and environmental concerns continue to rise, we count on our facility managers to take control of building/factory energy consumption. To reduce their companies’ carbon footprints, facility managers have begun implementing energy management programs to control their systems, optimize efficiency, and manage expenses.
But how are they doing it?
Let’s say you are trying to cool your facility. There are two steps to determining how much energy is consumed in the process. Read the rest of this entry »
Not all processes have optimal piping configurations. Learn how to identify alternative solutions for processes inhibited by piping constraints.
Siemens is hosting a free webinar on Wednesday, October 21 at 2pm EST.
In this 1-hour webinar, Siemens specialists will show you how the flowmeter can be installed and how this versatile instrument can be used to meet your application needs. They will be discussing the installation guidelines for process piping that can enhance your flowmeters’ performance.
The easy answer: Yes.
But in a recent webinar on choosing the best level technology for your application, the more specific answer is this: Yes, AS LONG AS you pay attention to the unit specs and a pretty simple rule of thumb.
Before I talk about the value of a universal 4-20mA analog output on a level controller, let me explain why anyone would care. It’s all about ground loops.
Since the early days of electronic instrumentation, way back when, even before cell phones or PCs, instrument people struggled with ground loops that create an offset error, drive the signal off scale, or burn up an analog circuit.
Lots of people like the pushbuttons on industrial pressure transmitters because the basic settings that every transmitter needs can be set up without a HART communicator. This includes things like the tag name, engineering units, LRV (Lower Range Value, the zero, or what 4.0mA represents), URV (Upper Range Value, the span, or what 20.0mA represents) and damping (an average or filter factor that dampens noise).
On the new Honeywell ST700/ST800 series smart transmitters, the tag name and engineering units are easy to configure and self explanatory, but I seem to stumble when setting up the LRV and URV because I’m faced with a non-descript choice. There’s two sets of options (under Transmitter Setup, not Calibration):
OK, either configures an LRV or a URV value, but which is which? What’s the difference?
When you’re making programming changes to a field device, you don’t always have time to wait. Here’s a hidden feature that helps you speed up the process between Siemens SIMATIC PDM and HART field instruments.
Normally, when you’re using PDM software, it takes a minute or so to upload or download changes to and from your HART devices. Seems like an eternity when all you need to do is change a range.
So, I’m going to let you in on a feature you might not have seen before.