Archive for category Configuration
Installing software on your PC isn’t hard. You click the .exe file and the software does its thing… right? Not always.
When it comes to Honeywell’s Trendview suite software, I’ve found that if you don’t take the extra step of running the install As Administrator, it produces faults in the software functionality after the install is complete. This holds true even if the user doing the install has administrative rights on the PC.
So, to help ensure a fault-free installation, make sure you do this:
Instead of double-clicking to launch the installer file, right-click on it.
Select Run as Administrator from the menu and follow the instructions.
Depending on your network setup, you may need to have an IT professional standing by to provide the administrator password.
As we’ve learned through trial and error, this is no longer an option to get the Trendview software to install properly: It’s mandatory to ensure a successful installation.
Lesman Instrument Company is the authorized Honeywell stocking distributor in Illinois, Indiana, Missouri, Paducah KY, Wisconsin, and Michigan’s Upper Peninsula. If you are located outside that area, you can find your local sales office or get technical assistance by visiting Honeywell’s contact page.
Dan Weise, Lesman product specialist, is an instructor for training classes on process instrumentation hardware, software, and technology.
Dan has been involved in all facets of data acquisition and process instrumentation since 1978, from sales and commissioning to service and support. He’s a long-time member of ISA, and has been with Lesman since 1988.
In his words, Dan’s the guy “who reads all the manuals nobody else reads”. In Lesman customers’ words, he’s the trainer to call if you want to “cut to the SO WHAT of instrumentation”, so it’s easy to understand.
Honeywell’s Process Instrument Explorer (PIE) configuration software used for configuring UDC controllers and the UDA analytical controller communicates with the instruments via RS-485, Ethernet, or Infrared (IR).
Since most newer PCs don’t ship with built-in serial ports to connect an IR adapter, you can use a USB-to-RS-232 converter, and then connect using the Actisys serial-to-infrared adapter (ACT-IR220L+). The USB converter will plug directly into your PC’s USB port, but install on a virtual COM port.
Here’s where it gets tricky: That COM port has to match the COM port used in PIE, and PIE doesn’t support ports above COM8.
Written by: Dan Weise
I couldn’t communicate with a HART device. The configuration software I was using, Pactware, thought the USB HART modem was on COM 3, while Windows’ Device Manager showed it was actually on COM 6.
To change the COM port in Pactware to COM 6, I right clicked COM 3 and selected Parameter:
Written by: Dan Weise
I’ve used Pactware for a couple years now, so I was surprised when I couldn’t get the Siemens LUT400 to work with the software. The LUT400 ultrasonic level and flow controller comes with a DTM file that I installed before opening the Pactware software.
The DTM file can be downloaded from this link: http://tinyurl.com/cqk2cky
Once it had been installed, I opened Pactware and updated the device catalog, as seen in the picture below:
But when I attempted to establish a HART connection to the LUT400, I got an error message: