Archive for category Communications
More and more people are using Modbus to get data from their instruments and controllers back into their control systems for reporting, alarming and troubleshooting.
And while I can’t be there to help you set up your Modbus master, I can give you 13 rules and some general practice advice for communicating to any Modbus RTU device.
It was bound to happen sooner or later.
I took a call from a customer who needed to replace a garden variety differential pressure transmitter… with one exception: He needed Honeywell’s DE digital protocol for communicating to his DCS. The DE protocol is still great, but since so many installations today use HART or Foundation Fieldbus, all of our in-stock pressure transmitters had a HART communication card – a critical mismatch to what the customer needed.
A year ago, we would have been stuck rush-ordering a unit from the factory, with all the attendant delays and expediting charges, because you couldn’t swap out a comms card without making the transmitter’s hazardous approval invalid.
What could we do?
Read the rest of this entry »
Before I talk about the value of a universal 4-20mA analog output on a level controller, let me explain why anyone would care. It’s all about ground loops.
Since the early days of electronic instrumentation, way back when, even before cell phones or PCs, instrument people struggled with ground loops that create an offset error, drive the signal off scale, or burn up an analog circuit.